DETERMINING YOUR ENERGY NEEDS BECAUSE WITH A POWER GENERATOR, SIZE MATTERS
thing you need to do is determine what size generator would work
best for your particular requirements. |
This section will help walk you through that process.
When purchasing a generator, it's important that you select one that's capable of meeting your energy requirements.
This section will assist you in estimating the power requirements so you can purchase the generator that will satisfy your needs.
Once you have the list, you can estimate the highest demand that will be put on the generator under the "worst-case" conditions. With this figure, you can determine the appropriate model Yamaha generator for your particular needs.
WARNING: Electrocution, severe personal injury or death can occur: Do not connect any generator to any building's electrical system unless an isolation switch has been installed by a licensed electrician. Refer to the Generator Owner's Manual.
CAUTION: Property damage can occur: Do not connect any generator to any building's electrical system unless an isolation switch has been installed by a licensed electrician. Refer to the Generator Owner's Manual.
TAKE IT STEP-BY-STEP
1. Identify the wattage requirements for the tools and appliances that you want to power. The power requirement for the tool or appliance can be found on its identification plate or in the Owner's Manual. If the power requirement is given in amps, multiply the amps times volts to derive the required watts.
Amps x Volts = Watts
2. Add up the required watts of all the tools and appliances you expect to operate simultaneously.
3. The total watts derived in step 2 is the size Yamaha generator you need. These three simple steps will "size" a generator. Normally, you won't need to consider motor starting requirements when using a Yamaha generator. When a Yamaha generator is properly sized for a tool's or appliance's running requirements, Yamaha's surge capability or 3 times the rated output for three seconds usually is sufficient to handle the motor's starting surge needs.
The Additional Guidelines section explains the procedures to calculate and size for motor starting.
Once you have compiled an accurate list of what you will be operating, you can calculate the maximum power requirements. There are three different calculations you can make, depending upon the kinds of tools and appliances on the list, and their intended use:
If your list does not include any devices that use electric motors, simply add the power (running) requirements of all the items on your list to obtain the maximum power needed.
NOTE: The EF1600's rated output is 1,400 watts, so its output would be too low to handle this load on a continuous basis.
*Running Watts is the amount of power a motor consumes once it has started to run at normal speed.
**932 is the factor used to convert motor horsepower ratings to needed electrical energy. It takes into account normal losses in utilizing that power.